Distributed generation, also distributed energy, on-site generation (OSG) or district/decentralized energy is electrical generation and storage performed by a variety of small, grid-connected or distribution system connected devices referred to as distributed energy resources (DER).
Conventional power stations, such as coal-fired, gas, and nuclear powered plants, as well as hydroelectric dams and large-scale solar power stations, are centralized and often require electric energy to be transmitted over long distances. By contrast, DER systems are decentralized, modular, and more flexible technologies, that are located close to the load they serve, albeit having capacities of only 10 megawatts (MW) or less. These systems can comprise multiple generation and storage components; in this instance they are referred to as hybrid power systems.
DER systems typically use renewable energy sources, including small hydro, biomass, biogas, solar power, wind power, and geothermal power, and increasingly play an important role for the electric power distribution system. A grid-connected device for electricity storage can also be classified as a DER system and is often called a distributed energy storage system (DESS). By means of an interface, DER systems can be managed and coordinated within a smart grid. Distributed generation and storage enables collection of energy from many sources and may lower environmental impacts and improve security of supply.
Microgrids are modern, localized, small-scale grids, contrary to the traditional, centralized electricity grid (macrogrid). Microgrids can disconnect from the centralized grid and operate autonomously, strengthen grid resilience, and help mitigate grid disturbances. They are typically low-voltage AC grids, often use diesel generators, and are installed by the community they serve. Microgrids increasingly employ a mixture of different distributed energy resources, such as solar hybrid power systems, which reduce the amount of emitted carbon significantly.
Historically, central plants have been an integral part of the electric grid, in which large generating facilities are specifically located either close to resources or otherwise located far from populated load centers. These, in turn, supply the traditional transmission and distribution (T&D) grid that distributes bulk power to load centers and from there to consumers. These were developed when the costs of transporting fuel and integrating generating technologies into populated areas far exceeded the cost of developing T&D facilities and tariffs. Central plants are usually designed to take advantage of available economies of scale in a site-specific manner, and are built as "one-off," custom projects.
These economies of scale began to fail in the late 1960s and, by the start of the 21st century, Central Plants could arguably no longer deliver competitively cheap and reliable electricity to more remote customers through the grid, because the plants had come to cost less than the grid and had become so reliable that nearly all power failures originated in the grid. Thus, the grid had become the main driver of remote customers' power costs and power quality problems, which became more acute as digital equipment required extremely reliable electricity. Efficiency gains no longer come from increasing generating capacity, but from smaller units located closer to sites of demand.
For example, coal power plants are built away from cities to prevent their heavy air pollution from affecting the populace. In addition, such plants are often built near collieries to minimize the cost of transporting coal. Hydroelectric plants are by their nature limited to operating at sites with sufficient water flow.
Distributed energy resources are mass-produced, small, and less site-specific. Their development arose out of:
Capital markets have come to realize that right-sized resources, for individual customers, distribution substations, or microgrids, are able to offer important but little-known economic advantages over central plants. Smaller units offered greater economies from mass-production than big ones could gain through unit size. These increased value--due to improvements in financial risk, engineering flexibility, security, and environmental quality--of these resources can often more than offset their apparent cost disadvantages. DG, vis-à-vis central plants, must be justified on a life-cycle basis. Unfortunately, many of the direct, and virtually all of the indirect, benefits of DG are not captured within traditional utility cash-flow accounting.
While the levelized cost of distributed generation (DG) is typically more expensive than conventional, centralized sources on a kilowatt-hour basis, this does not consider negative aspects of conventional fuels. The additional premium for DG is rapidly declining as demand increases and technology progresses, and sufficient and reliable demand may bring economies of scale, innovation, competition, and more flexible financing, that could make DG clean energy part of a more diversified future.
Distributed generation reduces the amount of energy lost in transmitting electricity because the electricity is generated very near where it is used, perhaps even in the same building. This also reduces the size and number of power lines that must be constructed.
Typical DER systems in a feed-in tariff (FIT) scheme have low maintenance, low pollution and high efficiencies. In the past, these traits required dedicated operating engineers and large complex plants to reduce pollution. However, modern embedded systems can provide these traits with automated operation and renewable energy, such as solar, wind and geothermal. This reduces the size of power plant that can show a profit.
Grid parity occurs when an alternative energy source can generate electricity at a levelized cost (LCOE) that is less than or equal to the end consumer's retail price. Reaching grid parity is considered to be the point at which an energy source becomes a contender for widespread development without subsidies or government support. Since the 2010s, grid parity for solar and wind has become a reality in a growing number of markets, including Australia, several European countries, and some states in the U.S.
Distributed energy resource (DER) systems are small-scale power generation or storage technologies (typically in the range of 1 kW to 10,000 kW) used to provide an alternative to or an enhancement of the traditional electric power system. DER systems typically are characterized by high initial capital costs per kilowatt. DER systems also serve as storage device and are often called Distributed energy storage systems (DESS).
DER systems may include the following devices/technologies:
Distributed cogeneration sources use steam turbines, natural gas-fired fuel cells, microturbines or reciprocating engines to turn generators. The hot exhaust is then used for space or water heating, or to drive an absorptive chiller  for cooling such as air-conditioning. In addition to natural gas-based schemes, distributed energy projects can also include other renewable or low carbon fuels including biofuels, biogas, landfill gas, sewage gas, coal bed methane, syngas and associated petroleum gas.
Delta-ee consultants stated in 2013 that with 64% of global sales, the fuel cell micro combined heat and power passed the conventional systems in sales in 2012. 20.000 units were sold in Japan in 2012 overall within the Ene Farm project. With a Lifetime of around 60,000 hours for PEM fuel cell units, which shut down at night, this equates to an estimated lifetime of between ten and fifteen years. For a price of $22,600 before installation. For 2013 a state subsidy for 50,000 units is in place.
In addition, molten carbonate fuel cell and solid oxide fuel cells using natural gas, such as the ones from FuelCell Energy and the Bloom energy server, or waste-to-energy processes such as the Gate 5 Energy System are used as a distributed energy resource.
Photovoltaics, by far the most important solar technology for distributed generation of solar power, uses solar cells assembled into solar panels to convert sunlight into electricity. It is a fast-growing technology doubling its worldwide installed capacity every couple of years. PV systems range from distributed, residential, and commercial rooftop or building integrated installations, to large, centralized utility-scale photovoltaic power stations.
The predominant PV technology is crystalline silicon, while thin-film solar cell technology accounts for about 10 percent of global photovoltaic deployment.:18,19 In recent years, PV technology has improved its sunlight to electricity conversion efficiency, reduced the installation cost per watt as well as its energy payback time (EPBT) and levelised cost of electricity (LCOE), and has reached grid parity in at least 19 different markets in 2014.
As most renewable energy sources and unlike coal and nuclear, solar PV is variable and non-dispatchable, but has no fuel costs, operating pollution, as well as greatly reduced mining-safety and operating-safety issues. It produces peak power around local noon each day and its capacity factor is around 20 percent.
Wind turbines can be distributed energy resources or they can be built at utility scale. These have low maintenance and low pollution, but distributed wind unlike utility-scale wind has much higher costs than other sources of energy. As with solar, wind energy is variable and non-dispatchable. Wind towers and generators have substantial insurable liabilities caused by high winds, but good operating safety. Distributed generation from wind hybrid power systems combines wind power with other DER systems. One such example is the integration of wind turbines into solar hybrid power systems, as wind tends to complement solar because the peak operating times for each system occur at different times of the day and year.
Hydroelectricity is the most widely used form of renewable energy and its potential has already been explored to a large extent or is compromised due to issues such as environmental impacts on fisheries, and increased demand for recreational access. However, using modern 21st century technology, such as wave power, can make large amounts of new hydropower capacity available, with minor environmental impact.
Modular and scalable Next generation kinetic energy turbines can be deployed in arrays to serve the needs on a residential, commercial, industrial, municipal or even regional scale. Microhydro kinetic generators neither require dams nor impoundments, as they utilize the kinetic energy of water motion, either waves or flow. No construction is needed on the shoreline or sea bed, which minimizes environmental impacts to habitats and simplifies the permitting process. Such power generation also has minimal environmental impact and non-traditional microhydro applications can be tethered to existing construction such as docks, piers, bridge abutments, or similar structures.
Municipal solid waste (MSW) and natural waste, such as sewage sludge, food waste and animal manure will decompose and discharge methane-containing gas that can be collected and used as fuel in gas turbines or micro turbines to produce electricity as a distributed energy resource. Additionally, a California-based company, Gate 5 Energy Partners, Inc. has developed a process that transforms natural waste materials, such as sewage sludge, into biofuel that can be combusted to power a steam turbine that produces power. This power can be used in lieu of grid-power at the waste source (such as a treatment plant, farm or dairy).
A distributed energy resource is not limited to the generation of electricity but may also include a device to store distributed energy (DE). Distributed energy storage systems (DESS) applications include several types of battery, pumped hydro, compressed air, and thermal energy storage.:42 Access to energy storage for commercial applications is easily accessible through programs such as energy storage as a service (ESaaS).
For reasons of reliability, distributed generation resources would be interconnected to the same transmission grid as central stations. Various technical and economic issues occur in the integration of these resources into a grid. Technical problems arise in the areas of power quality, voltage stability, harmonics, reliability, protection, and control. Behavior of protective devices on the grid must be examined for all combinations of distributed and central station generation. A large scale deployment of distributed generation may affect grid-wide functions such as frequency control and allocation of reserves. As a result, smart grid functions, virtual power plants  and grid energy storage such as power to gas stations are added to the grid.
Each distributed generation resource has its own integration issues. Solar PV and wind power both have intermittent and unpredictable generation, so they create many stability issues for voltage and frequency. These voltage issues affect mechanical grid equipment, such as load tap changers, which respond too often and wear out much more quickly than utilities anticipated. Also, without any form of energy storage during times of high solar generation, companies must rapidly increase generation around the time of sunset to compensate for the loss of solar generation. This high ramp rate produces what the industry terms the duck curve (example) that is a major concern for grid operators in the future. Storage can fix these issues if it can be implemented. Flywheels have shown to provide excellent frequency regulation. Also, flywheels are highly cyclable compared to batteries, meaning they maintain the same energy and power after a significant amount of cycles( on the order of 10,000 cycles). Short term use batteries, at a large enough scale of use, can help to flatten the duck curve and prevent generator use fluctuation and can help to maintain voltage profile. However, cost is a major limiting factor for energy storage as each technique is prohibitively expensive to produce at scale and comparatively not energy dense compared to liquid fossil fuels. Finally, another necessary method of aiding in integration of photovoltaics for proper distributed generation is in the use of intelligent hybrid inverters. Intelligent hybrid inverters store energy when there is more energy production than consumption. When consumption is high, these inverters provide power relieving the distribution system.
Another approach does not demand grid integration: stand alone hybrid systems.
There have been some efforts to mitigate voltage and frequency issues due to increased implementation of DG. Most notably, IEEE 1547 sets the standard for interconnection and interoperability of distributed energy resources. IEEE 1547 sets specific curves signaling when to clear a fault as a function of the time after the disturbance and the magnitude of the voltage irregularity or frequency irregularity. Voltage issues also give legacy equipment the opportunity to perform new operations. Notably, inverters can regulate the voltage output of DGs. Changing inverter impedances can change voltage fluctuations of DG, meaning inverters have the ability to control DG voltage output. To reduce the effect of DG integration on mechanical grid equipment, transformers and load tap changers have the potential to implement specific tap operation vs. voltage operation curves mitigating the effect of voltage irregularities due to DG. That is, load tap changers respond to voltage fluctuations that last for a longer period than voltage fluctuations created from DG equipment.
Many authors now think that these technologies may enable a mass-scale grid defection because consumers can produce electricity using off grid systems primarily made up of solar photovoltaic technology. For example, the Rocky Mountain Institute has proposed that there may wide scale grid defection. This is backed up by studies in the Midwest.
Cogenerators are also more expensive per watt than central generators. They find favor because most buildings already burn fuels, and the cogeneration can extract more value from the fuel . Local production has no electricity transmission losses on long distance power lines or energy losses from the Joule effect in transformers where in general 8-15% of the energy is lost (see also cost of electricity by source).
Some larger installations utilize combined cycle generation. Usually this consists of a gas turbine whose exhaust boils water for a steam turbine in a Rankine cycle. The condenser of the steam cycle provides the heat for space heating or an absorptive chiller. Combined cycle plants with cogeneration have the highest known thermal efficiencies, often exceeding 85%.
In countries with high pressure gas distribution, small turbines can be used to bring the gas pressure to domestic levels whilst extracting useful energy. If the UK were to implement this countrywide an additional 2-4 GWe would become available. (Note that the energy is already being generated elsewhere to provide the high initial gas pressure - this method simply distributes the energy via a different route.)
A microgrid is a localized grouping of electricity generation, energy storage, and loads that normally operates connected to a traditional centralized grid (macrogrid). This single point of common coupling with the macrogrid can be disconnected. The microgrid can then function autonomously. Generation and loads in a microgrid are usually interconnected at low voltage and it can operate in DC, AC, or the combination of both. From the point of view of the grid operator, a connected microgrid can be controlled as if it were one entity.
Microgrid generation resources can include stationary batteries, fuel cells, solar, wind, or other energy sources. The multiple dispersed generation sources and ability to isolate the microgrid from a larger network would provide highly reliable electric power. Produced heat from generation sources such as microturbines could be used for local process heating or space heating, allowing flexible trade off between the needs for heat and electric power.
GTM Research forecasts microgrid capacity in the United States will exceed 1.8 gigawatts by 2018.
Micro-grids have seen implementation in a number of communities over the world. For example, Tesla has implemented a solar micro-grid in the Samoan island of Ta'u, powering the entire island with solar energy. This localized production system has helped save over 100,000 gallons of diesel fuel. It is also able to sustain the island for three whole days if the sun were not to shine at all during that period. This is a great example of how micro-grid systems can be implemented in communities to encourage renewable resource usage and localized production.
To plan and install Microgrids correctly, engineering modelling is needed. Multiple simulation tools and optimization tools exist to model the economic and electric effects of Microgrids. A widely used economic optimization tool is the Distributed Energy Resources Customer Adoption Model (DER-CAM) from Lawrence Berkeley National Laboratory. Another frequently used commercial economic modelling tool is Homer Energy, originally designed by the National Renewable Laboratory. There are also some power flow and electrical design tools guiding the Microgrid developers. The Pacific Northwest National Laboratory designed the public available GridLAB-D tool and the Electric Power Research Institute (EPRI) designed OpenDSS to simulate the distribution system (for Microgrids). A professional integrated DER-CAM and OpenDSS version is available via BankableEnergy. A European tool that can be used for electrical, cooling, heating, and process heat demand simulation is EnergyPLAN from the Aalborg University, Denmark.
On 11 October 2017, California Governor Jerry Brown signed into law a bill, SB 338, that makes utility companies plan "carbon-free alternatives to gas generation" in order to meet peak demand. The law requires utilities to evaluate issues such as energy storage, efficiency, and distributed energy resources.